Light bulbs up to 2000 W
LED lamps up to 200 W
1 closing contact not isolated 10 A/250 V/AC, incandescent bulbs up to 2000 W, ESL and LED-lamps up to 200W, switch-off pre-warning and scanner light can be attached. By-Verlust of only 0.7 W. With ESL-optimization. For mounting. 45 mm long, 55 mm wide, 18 mm deep.
Contact switching in the zero crossing to protect the contacts and lamps. In particular, this extends the life span of energy-saving lamps. Through the use of a bi-stable relay, there are also when it is switched on, no coil power loss and no heat build-up in this way. After installing the automatic short synchronization wait before the consumer connected downstream of the power. Control-, supply and switching voltage 230 V. Time setting 1 to 12 minutes. Glow lamp current up to 50 mA, depending on the starting voltage of the glow lamps. For 3- and 4-wire circuits, Resetteable, with roof floor lighting at
4-wire circuit. Automatic detection of the type of connection. After a power failure, the lighting is switched on again when the time is not yet complete. The light flickers at trains = unconnected switch-off pre-warning about 30 seconds before time expiry starting and a total of 3 times in shorter time intervals. With added scanner light can be placed buttons for more than 1 second for continuous light, which switches itself off automatically after 60 minutes or with button for longer than 2 seconds can be switched off. Are scanner light and switch-off pre-warning, takes place after switching off the continuous light only the switch-off pre-warning. Be wholly or partially energy saving lamps ESL switched, then the switch-off pre-warning with scanner light ESL on the lower rotary switch setting. Within the first second after switching on or after can switch in the tlz functions the time by up to 3 times short keys can be extended. Each keys added 1 times the set time. The ESV, power surge switch with fall-back delay up to 120 minutes, switchable. In this function, after the end of the adjustable delay time is switched off automatically, when the manual off command not been given. In the function ESV, the delay time set to the minimum, the delay is turned off and there is the normal surge current switch function.
4010312400791, Eltako, 61100102, TLZ61NP-230V